The paper "Fire Safety & Risk Assessment for the Anywhere Community Centre" is a perfect example of a finance and accounting assignment. This report comprises two parts and provides an overall assessment of and general plan for fire safety at the Anywhere Community Centre. The first part describes the configuration of the building, assesses its resistance to fire spread, describes appropriate detection, alarm, and fire-fighting features, and details evacuation paths from the building. The second part discusses a plan for maintaining fire safety at the Community Centre, including staff training, attention to special conditions in the facility, and significant upgrades that must be made to the building. Part One: Fire Safety Strategy 1.1 Stability of the Structure The overall stability of the structure is dependent on the internal and external resistance to fire spread, which is detailed in the following two sections.
The general interior configuration of the Anywhere Community Centre is a single-level, vaulted space arranged around a large central hall. In general, the large masonry construction of the Anywhere Community Centre provides a robust structure that should not aggravate fire spread, and remain stable for a long period of time even in a severe fire.
The one exceptional area of concern is the wood-plank style ceiling throughout the building, which does not meet applicable guidelines. A second concern is the need to ensure that appropriate cavity barriers are installed in the external walls since the building plan diagram does not indicate their presence. 1.2 Internal Fire Spread Flooring is of vinyl asbestos throughout the building, except for the lobby (fore or east portion of the entry hall) and a chapel portion of the central hall, which are floored with quarry tile; the stage and assembly areas of the central hall, which are timber-floored; and the boiler and oil storage spaces, which have granolithic flooring.
Interior walls and lintels consist of concrete hollow blocks. The ceiling is 19 mm tongue-and-groove softwood boarding. Paragraph B2.ii of Approved Document B, Volume 2 Buildings other than DwellInghouses, Building Regulations 2006 (p. 63) exempts the upper surface of floors from the regulations because they are not significantly involved in a fire until its later stages.
Fire safety risk assessment: small and medium places of assembly. (PDF document) London: Department for Communities and Local Government, 2006. Available from:
Approved Document B, Volume 2 – Buildings other than dwellinghouses. (PDF document) London: Department for Communities and Local Government, April 2007. Available from: